Quick and easy access to recreational privileges in Iowa, including hunting, fishing, and specialty licenses:
Purchase Your Licenses Online
Buy your Hunting and Fishing license online today! We offer multi-year packages and combos for whatever you need to stay licensed.
Support conservation in Iowa by buying a natural resource plate for your vehicle.
Make your online reservation for state park cabins, camping sites and lodges.
Iowa DNR Customer Service
Mon - Fri, 8:00am - 4:30pm CST
Submit Online Inquiry
Information / Records Requests
Contact Information by County
Underground storage tanks and piping constructed with steel or other metal in direct contact with the soil must be protected from corrosion with a cathodic protection system. This includes piping steel flex connectors in contact with the soil.
These cathodic protection systems are required to have a complete inspection every three years by a qualified cathodic protection tester. The Cathodic Protection System Inspection Report form must be used by the tester to record the results of the system inspection. The form and the testers report must be kept as part of the records and be available for review by the compliance inspectors.
Tank owners/operators with an impressed current cathodic protection system are required to read the ampere and voltage meters on the rectifier at least every 60 days. These readings must be kept as part of the site’s records and made available to the cathodic protection tester for the three year system test. This chart may be used to record the rectifier readings.
You will need Adobe Acrobat Reader to view the .pdf file. Click on the icon at the bottom of this screen to download Acrobat Reader. The .doc files are Word documents and may be completed electronically.